Power transformer diagnostics
FKH offers on-site diagnostic measurements for both new and service-aged power transformers. For measurements in connection with commissioning, the focus is on inspection of assembly, installation and oil impregnation, and also on characterisation of the transformer for subsequent comparisons (fingerprint in new condition). Diagnostic measurements on service-aged transformers are used to determine the condition of the insulation and to arrive at decisions regarding continued operation, the need for maintenance measures and planning of future inspections.
FKH has offered diagnostic measurements on transformers since the 1990s. During this period, important basic knowledge was built up under the auspices of a project undertaken jointly with Switzerland’s technical colleges and universities, sponsored by the Project and Study Foundation of the Swiss Electricity Companies (PSEL).
Test methods offered
High-voltage partial discharge tests with electrical and acoustic detection during external voltage application or induced voltage testing
Offline partial discharge measurement is the most meaningful test for the detection of local weak points in the insulation and is used to identify faults.
Short-circuit and open-circuit impedance measurements
These measurements allow direct comparisons with the factory acceptance measurements so that major faults on the windings and the core are identified.
Frequency response analysis (FRA)
Frequency response analysis or FRA is a comparative method that indicates geometric changes to windings, caused (for example) by short-circuit forces or shocks and vibrations during transportation.
This measurement is used to detect any coil short-circuits or faults on the onload tap changer.
PDC measurement; analysis of polarisation and depolarisation currents
This method is used to determine the proportion of polarisable substances in the insulation. This makes it possible to estimate the water content in the pressboard.
DC (Direct Current)- resistance measurement
This measurement identifies changes of resitance and coil short-circuits. Contact resistances can also be determined. Recording the switching operations performed by onload tap changers (dynamic measurement) makes it possible to assess whether the contacts are switching correctly.
C-tan(δ) measurement of bushings
This measurement is used to determine the ageing condition of the bushing insulation.
Measurements of switch-on current provide information about the interaction between the transformer core, the grid and the protective devices, and also about the mechanical stress on the windings when the transformer is switched on.
Oil analyses (e.g. dielectric-chemical oil analysis, gas-in-oil analysis, furan analysis)
Procedures to analyse oil deliver specific information about many aspects of the condition of the insulation: general condition of the oil, fault detection based on the composition of the dissolved gases, indications of cellulose decomposition and other ageing processes (For more details, see Insulating oil analyses)